This tutorial explains the three most commonly used boiler ratings: The 'From and at' rating for evaporation, the kW rating for heat output, and boiler horsepower.
Boiler Ratings
The application of the ‘from and at’ rating graph (Figure 3.5.1) is shown in Example 3.5.1, as well as a demonstration of how the values are determined.
Example 3.5.1
A boiler has a ‘from and at’ rating of 2 000 kg/h and operates at 15 bar g. The feedwater temperature is 68°C.
The use of Equation 3.5.1 will determine a factor to produce the same result:
Note: These values are all from steam tables.
Using the information from Example 3.5.1 and the Equation 3.5.1 the evaporation factor can be calculated:
kW rating
Some manufacturers will give a boiler rating in kW. This is not an evaporation rate, and is subject to the same ‘from and at’ factor.
To establish the actual evaporation by mass, it is first necessary to know the temperature of the feedwater and the pressure of the steam produced, in order to establish how much energy is added to each kg of water. Equation 3.5.2 can then be used to calculate the steam output:
Example 3.5.2
A boiler is rated at 3 000 kW (kJ/s) and operates at 10 bar g with a feedwater temperature of 50°C. How much steam can be generated?
Where, from using the tables on the Spirax Sarco website:
Boiler horsepower (BoHP)
This unit tends to be used only in the USA and Australia. A boiler horsepower is not the commonly accepted 550 ft lbf/s and the generally accepted conversion factor of 746 Watts = 1 horsepower does not apply.
USA and Australia
In the USA and Australia the readily accepted definition of a boiler horsepower is the amount of energy required to evaporate 34.5 lb of water at 212°F atmospheric conditions.
Example 3.5.3
A boiler is rated at 500 BoHP, what is its steam output?
Important: This is essentially the same as a ‘from and at’ rating, so using feedwater at lower temperatures and steam at higher pressures will reduce the amount of steam generated.
In practice: A BoHP figure of 28 to 30 lb / h would be a more realistic maximum continuous rating, taking into account the steam pressure and average feedwater temperatures.
A more practical result would then be:
Consequently: If 17 250 lb/h of steam is required, a 500 BoHP boiler would be too small, and the user would need to specify a boiler with a rating of: